Air Conditioner Review
Replacement solenoid for many brands/models of whole house humidifiers. Same as Aprilaire 4040. Bryant:HUMBBSBP2412-A27HUMBBLBP2417-A24HUMBBLFP1418-A24HUMBBWBP2417-A24 Carrier:HUMCCSBP2412-A27HUMCCLBP2417-A24HUMCCLFP1418-A24HUMCCWBP2417-A24Totaline: P110-SBP2412P110-LBP2417P110-LFP1418ICP: HMICSB12BHMICLB17BHMICLF18B Lennox:HCWB3-12HCWB3-17HCWP3-18HCWB3-12AHCWB3-17AHCWP3-18A Trane:THUMD200ABM00BATHUMD300ABA00BATHUMD500APA00BA American Standard:AHUMD200ABM00BAAHUMD300ABA00BAAHUMD500APA00BA Nordyne:917897091786309178640 Maytag:918127091812809181290 York:S1-BP5000MYS1-BP6000MYS1-FP7000MY Coleman:S1-BP5000MCS1-BP6000MCS1-FP7000MC Luxaire:S1-BP5000MLS1-BP5000MLS1-BP6000MLS1-FP7000ML 24 VAC 2.3 Watts Replacement solenoid value for newer Bryant Carrier Humidifiers. Valve includes a new inline strainer (pre-inserted in inlet side of valve), and a compression nut & washer for the inlet side only. Solenoid Valve Replacement Instructions For power units unplug electrical cord. For bypass units turn off power to furnace. Also turn the humidistat off. Shut off water supply at the saddle valve Disconnect inlet and outlet water compression nuts. Double wrench. Note, some water may drip on floor. Remove the orifice (which controls the water flow) from the plastic or copper tube and make sure there is no obstruction. If blocked clean or replace. Remove the wire nuts from the water solenoid valve wire connections. Set aside. Remove screws that secure valve to unit. Attach new valve with screws. Do not over-torque screws into plastic housing. Reconnect wires with wire nuts. For units with plastic feed tubes inspect for brittleness, hairline cracks, nicks or abrasions, etc. Replace if necessary. Reconnect the water lines, double wrenching the compression nuts. Turn water back on and check system for leaks. Tighten compression nuts as necessary. Restore electrical service and a
No features available.
List Price: $64.95
Sale Price: $64.95
Air Availability: Usually ships in 1-2 business days